The storage of water at high temperature removes one possible breeding ground for Legionella; the use of a thermostat, rather than a static mixing valve, provides increased safety against scalding, and increased user comfort, because the hot-water temperature remains constant.
Many TMVs use a wax thermostat for regulation. They also shut off rapidly in the event of a hot or cold supply failure to prevent scalding or thermal shock.
It is increasingly common practice around the world to regulate the storage water temperature to above 60 °C (140 °F), and to circulate or distribute water at a temperature less than 50 °C (122 °F). Water above these temperatures can cause scald injuries. Many countries, states, or municipalities now require that the temperature of all bath water in newly built and extensively refurbished domestic properties be controlled to a maximum of 48 °C (118 °F). Installing thermostatic mixing valves can ensure that water is delivered at the required temperature, thereby reducing the risk of scalding accidents; it also reduces hot water consumption from a supply that is maintained at a higher temperature.
There are three main categories for water temperature controlling devices: Heat Source, Group Control, and Point-of-Use.
These are used with central heating systems that use water as a medium.
· Tempering valves for use on hot water heat distribution systems
· High flow rates suitable for use in under floor (radiant) heating applications
· Allows water to be stored at a higher temperature
These provide a uniform distribution temperature for all hot water outlets in a household.
· Designed for multi-point applications
· High flow rates (from 14 gpm to 51 gpm at 45 psi)
· Temperature stability
These are single Outlet Thermostatic Mixing Valves, often called "thermostatic faucets", "thermostat taps" or "thermostat valves".
· Designed for single point applications, such as individual showering, hand wash basin mixers, bath or tub fillers
· High level protection against scalding and thermal shock
Although other temperature regulating valves exist, thermostatic mixing valves are the preferred type in health care facilities, as they limit maximum outlet temperature, regardless of pressure or flow.
Related Industry Knowledge
- The replacement is very fast
- It is best to change regularly at the same time
- Extend the service life of shower faucets and s...
- Effectively prevent the hose from entangling an...
- Strong anti-scale and anti-fouling ability
- Greatly improves the safety and comfort of the ...
- How to use can improve life
- Meet people's special use requirements
- Reducing the trouble of replacing the faucet an...
- Essential household appliances for modern famil...
- brass faucet inspection by consumer-VIP tips
- 304 stainless steel faucet inspection method by...
- How to polish the faucet and iwater polish proc...
- How to choose an instant hot water tap or dispe...
- Introduction of Iwater revolutionary electric i...
- Understanding sintered activated carbon filter
- Basic terms and names of clean water
- The difference between ultrafiltration, nanofil...
- How to identify the advantages and disadvantage...
- graphic expression for instant boiling water ta...